Yokogawa flange mounted differential pressure transmitter price EJA210E-JMS4G-912NN-EA13B1WE03-B/FU1
The high performance flange mounted differential pressure transmitter EJA210E can be used to measure levels of densities of solidifying or precipitating liquids. EJA210E outputs a 4 to 20 mA DC signal corresponding to the measured differential pressure. Its accurate and stable sensor can also measure the static pressure which can be shown on the integral indicator or remotely monitored via BRAIN or HART communications. Other key features include quick response, remote set-up using communications and self-diagnostics. FOUNDATION Fieldbus, PROFIBUS PA and 1 to 5 V DC with HART (Low Power) protocol types are also available. All EJA-E series models in their standard configuration, with the exception of the Fieldbus, PROFIBUS and Low Power types, are certified as complying with SIL 2 for safety requirement.
The EJA-E series of transmitters is Yokogawa's most recent evolution of the DPharp family of pressure transmitters. Released in 2012, it combines the ruggedness and success of the work-horse EJA-A series with the performance of the thoroughbred EJX-A series to deliver the type of product you have come to expect from Yokogawa.
The EJA210E is the Flange-mount Liquid Level Transmitter in the series.
EJA210E features include:
± 0.075% Accuracy
± 0.1% per 1 year Stability
120 msec Response Time
Exida and TUV SIL2 / SIL3 Certified
Signal Characterizer for the 4 to 20 mA output
Local Parameter Setting (LPS)
|EJA210E||Flange mounted differential pressure transmitter|
|J||4 to 20 mA DC with digital communication (HART 5/HART 7 protocol)*1|
|M||1 to 100kPa (4 to 400 inH2O)|
|S||Refer to “Low Pressure Side Wetted Parts Materials” Table.|
|4||with 1/2 NPT female process connector|
|9||Horizontal piping type and left side high pressure|
|1||Cast aluminum alloy|
|2||1/2 NPT female, two electrical connections without blind plugs|
|A1||ANSI class 150|
|B||304 SST *6|
|1||Serration (for ANSI flange only)|
|WE||Hastelloy C-276 *4# 316 SST# 316 SST#|
|3||Length (X2) = 100mm|
|B||For general use (Silicone oil) –40 to 120°C –40 to 85°C|
|/FU1||Combined FF1 and FS1 *1 *3|
*1: HART 5 or HART 7 is selectable. Specify upon ordering.
*2: Not applicable for electrical connection code 0, 5, 7, 9 and A.
*3: Not applicable for electrical connections code 0, 5, 7 and 9.
*4: Material of a blind plug; aluminum alloy for code 5 and 9, and SUS304 for code 7.
*5: Not applicable for output signal code G.
*6: Not applicable for output signal code F.
*7: As CE marking is still pending, not applicable for those countries which require CE marking.
*1: Not applicable for amplifier housing code 2 and 3.
*2: Not applicable with color change option. Not applicable for amplifier housing code 2.
*3: 316 or 316L SST. The specification is included in amplifier code 2.
*4: Applicable only when fill fluid code -D is specified.
*5: The unit of MWP (Max. working pressure) on the name plate of a housing is the same unit as specified by option code D1,
D3, and D4.
*6: Applicable for flush type (process connection style code W.)
*7: Applicable for flushing connection ring code 0.
*8: Applicable for output signal code D and J. The hardware error indicates faulty amplifier or capsule.
*9: Applicable for wetted parts material code SW, SE, WW, WE, and HW.
Consult Yokogawa in case gold-plated diaphragm is required for low pressure side.
*10: Also see ‘Ordering Information.’
*11: Applicable for Low Pressure Side Process connection code 0 and 5.
*12: Applicable for Low Pressure Side Process connection code 1, 2, 3, and 4.
*13: Applicable for flushing connection ring code A, B, C, and D.
*14: The unit on the certificate is always MPa regardless of selection of option code D1, D3, or D4.
*15: A flushing connection ring will not be applied when conducting the pressure test or leak test.
*16: Applicable for extended type (process connection style code E.)
*17: Pure nitrogen gas is used for oil-prohibited use (option code K1, K2, K5, and K6.)
*18: The 1 to 5 V voltage output corresponding to 4 to 20 mA current output is applied to output signal code Q which is noncompliant
to NAMUR NE43.