YOKOGAWA EJA110E-JMS4J-912DB/D3 4 to 20 mA Differential pressure transmitter
The EJA-E series of transmitters is Yokogawa's most recent evolution of the DPharp family of pressure transmitters. Released in 2012, it combines the ruggedness and success of the work-horse EJA-A series with the performance of the thoroughbred EJX-A series to deliver the type of product you have come to expect from Yokogawa.
The EJA110E is our standard traditional-mount differential pressure transmitter in this series.
EJA110E features include:
0.055% Accuracy (0.04% Accuracy optional)
0.1% Stability per 10 years
90 ms Response Time
Exida and TUV SIL 2 / SIL3 Certified
MWP 2,300 psi (MWP 3,600 psi option)
Local Parameter Setting (LPS)
|EJA110E||Differential pressure transmitter|
|J||4 to 20 mA DC with digital communication (HART 5/HART 7 protocol)*1|
|M||1 to 100 kPa (4 to 400 inH2O)|
|S||Refer to “Wetted Parts Material” Table|
|4||with 1/2 NPT female process connector|
|J||B7 carbon steel|
|9||Horizontal piping and left side high pressure|
|1||Cast aluminum alloy|
|2||1/2 NPT female, two electrical connections without blind plugs|
|B||304 SST 2-inch pipe mounting, flat type (for horizontal piping)|
|/D3||bar calibration (bar unit)|
*1: HART 5 or HART 7 is selectable. Specify upon ordering.
*2: Users must consider the characteristics of selected wetted parts material and the influence of process fluids. The use of
inappropriate materials can result in the leakage of corrosive process fluids and cause injury to personnel and/or damage
to plant facilities. It is also possible that the diaphragm itself can be damaged and that material from the broken diaphragm
and the fill fluid can contaminate the user’s process fluids.
Be very careful with highly corrosive process fluids such as hydrochloric acid, sulfuric acid, hydrogen sulfide, sodium
hypochlorite, and high-temperature steam (150°C [302°F] or above). Contact Yokogawa for detailed information of the
wetted parts material.
*3: Only applicable for Wetted parts material code S.
*4: Not applicable for measurement span code F.
*5: Not applicable for electrical connection code 0, 5, 7, 9 and A.
*6: Not applicable for electrical connection code 0, 5, 7 and 9.
*7: Material of a blind plug; aluminum alloy for code 5 and 9, and SUS304 for code 7.
*8: Not applicable for output signal code G.
*9: Not applicable for output signal code F.
What are the four major measurements for process control?
1. Pressure 2. Flow 3. Level 4. Temperature
How is the EJA-E different than EJA-A series?
EJA-E series offers enhanced performance in terms of Reference accuracy, Response time, Multi-sensing, Long term stability
What is the Reference Accuracy (%span) of the EJA110E and the EJA115E?
The Reference Accuracy (%span) is +/- 0.055%. For the EJA110E - only for wetted parts material code: S. Wetted parts material code "S" is Hastelloy C-276 Diaphragm, 316 SST Capsule, Flanges, Vent and Drain
What is the Reference Accuracy (%span) of the EJA130E?
The Reference Accuracy (%span) is +/- 0.055%.
What is the Reference Accuracy (%span) of the EJA430E?
The Reference Accuracy (%span) is +/- 0.055%. Only for the wetted parts material code: S.Wetted parts material code "S" is Hastelloy C-276 Diaphragm, 316 SST Capsule, Flanges, Vent and Drain
What is the Reference Accuracy (%span) of the EJA440E?
The Reference Accuracy (%span) is +/- 0.055%. This is an enhancement over the EJA-A series 440 which is +/- 0.12%
What is the Reference Accuracy (%span) fo the EJA310E?
The Reference Accuracy (% span) for the EJA310E is +/- 0.1%. This applies to the "M", "A" and "B" capsule.
What is the Reference Accuracy (%span) of the EJA510/530E?
The Reference Accuracy (%span) for the EJA510/530E is +/- 0.15%
What is the Range of the new "H" capsule for the Gauge EJA430E?
The Range for the new "H" capsule for the Guage EJA430E is -400 to +2,000 inH2O.
What is the Range of the new "B" Capsule for the Absolute EJA310E?
The Range of the new "B" Capsule for the Absolute EJA310E is 0 to 2,300 psia.
What is the Long term Stability period for the EJA-E series?
The Long term Stability period for the EJA-E series is 0.1% of URL per 7 years.
What CSA approval codes are available for the EJA-E?
In addition to the /CF1 option, we now have the /CS1 and /CU1 options for CSA approval codes. /CS1 option includes the following: CSA Intrinsically safe ApprovalCertificate: 1606623 [For CSA C22.2]Intrinsically S.
What is the EJA-E series
EJA-E is Yokogawa's new transmitter series for enhancement of our Dpharp line-up. It follows the basic construction of the existing EJX series with improved specifications compared to the EJA-A series.
Why is the EJA_E different than EJX but looks the same ?
Although the basic construction of the EJA-E is similar to the EJX series, the actual manufacturing processes like sensorcharacterization, calibration / verification are different.